Bid Alert No: 00000507569
Bid Title: COMMERICAL EVAPORATIVE COOLER FOR AIR OPS.
Agency Bid No. Title: RFB-IS-16201102
Received Date: 03/09/2016
Close Date: 03/22/2016
Purchase Type: Not Stated
Delivery Point: Warehouse, 12605 Osborne Street, Pacoima, California, 91331
Delivery Date: Not Stated
Specifications include, but are not limited to: Commercial Evaporative Cooler and PartsA.Commercial Evaporative Coolers (part number H2231) or Equal and that are side discharge. Dimensions are 60 Height x 62 Width x 62 Depth, with the side discharge opening of 31 3/4 x 31 3/4. The opening is 23 3/4 from the bottom and centered at 15 1/8 from the sides. Belt and Aspen filters are included or equivalent. B.Three-Phase Open Drip proof Motor (part number D2P2D). or EqualAgency Certification: UR/CSA/CE; Ambient Operating Temp. (Celsius): 40; Bearing Type: Ball; Efficiency: 86.5; Efficiency Level: PRE; Enclosure: ODP; F/L Amps: 5.5; HP: 2; Hz: 50/60; Insulation Class: F; Mounting: Rigid Base; NEMA Frame: 145T; Phase: Three; RPM: 1800; Service Factor: 1.15; Shaft Diam.: 7/8"; Shaft Length: 2 1/4"; Std. Mount. Pos.: F-1; Thermal Protection: None; Volts: 208-230/460 or equivalent.C.2 BK Cast Iron Sheave (part number 2VP42X7/8). Or EqualHub Bore: 7/8"; O.D.: 3.95"; Pitch Diam. 3L Belt: 2.5"-3.3"; Pitch Diam. A Belt: 2.63.6"; Pitch Diam. B Belt: 2.93.9"; Pitch Diam. O Belt: 2.703.50" or equivalent.D.Evaporative Cooler Pump (part number CP3-230). Or EqualGPH @ 1': 563; GPH @ 10': 231; GPH @ 3': 512; GPH @ 5': 460; Height: 9"; HP: 1/30; Max. CFM: 21,000; Shutoff: 12.0'; Volts: 230; or equivalent.E.Float Valve (part number 4164). Or Equal3/8" compression valve for industrial coolers. Heavy-duty corrosion resistant bronze body, brass plunger, arm and stem. Polypropylene float, two-piece arm with adjustable screw or equivalent.
Product Code: 03138
Issuing Agency: County of Los Angeles
Agency Type: State and Local
Contact: Bryce Kiriyama 1100 N. Eastern Avenue, Room 103, Los Angeles, California, 90063